Specifications:927/927138-got2000_series.pdf file (07 Aug 2023)
Mitsubishi Electric GOT2000 Series Computer Hardware, Graphics Tablet PDF Connection Manual (Updated: Monday 7th of August 2023 03:58:34 PM)
Rating: 4.7 (rated by 73 users)
Compatible devices: GT1155HS-QSBD, DX-TL5000E, GT1695M-XTBD, DIAMOND DIGITAL DV175, LDT422V, GT1020-LBD, DPro930SB-BK, F920GOT-K.
401, 9.4 GOT Side Settings 9 - 11 CONNECTION TO SHARP PLC 9 9.4.2 Communication detail settings Make the settings according to the usage environment. *1 When connecting to the communication port, set "Delay Time" of the GOT side to 30ms or more. POINT POINT POINT (1) Communication interface setting by the Utility The communication interface setting can be changed on the Utility's [Communication Settings] after writing [Communication Settings] of project data. For details on…
259, Mitsubishi Electric GOT2000 Series 4.3 Ethernet Connection 4 - 57 4 CONNECTION TO OMRON PLC ■2. Communication Setting for NJ series For the PLC communication setting, set with an automation software Sysmac Studio. (1) Setting of an automation software Sysmac Studio *1 Adjust the settings with the Ethernet settings of the GOT side. ➠ (2) EtherNet/IP (OMRON NJ), Gateway *2 Adjust the settings with the GOT Ethernet settings of the GOT side. ➠ 1.1.2…
556, 15 - 26 15.3 Connection Diagram 15.3 Connection Diagram The following diagram shows the connection between the GOT and the PLC. 15.3.1 RS-232 cable ■1. Connection diagram (1) RS-232 connection diagram 1) (2) RS-232 connection diagram 2) (3) RS-232 connection diagram 3) GOT side PLC side CD RD(RXD) SD(TXD) ER(DTR) SG DR(DSR) RS(RTS) CS(CTS) - 1 2 3 4 5 6 7 8 9 1 3 2 4 7 5 6 8 20 FG RD SD RS SG CS DR CD ER GOT side PLC side CD RD(RXD) SD(TXD) ER(DTR) SG DR(DSR) RS(RT…
379, 8.3 Connection Diagram 8 - 13 8 CONNECTION TO JTEKT PLC (7) RS-422 connection diagram 7) *1 Terminating resistors should not be provided for a PLC and an RS-232/RS-422 interface converter which will be terminals. *2 Set the terminating resistor of GOT side which will be a terminal. ➠ ■3. Connecting terminating resistors *3 Connect FG grounding to the appropriate part of a cable shield line. ■2. Precautions when preparing a cable (1) Cable length The maximum lengt…
544, 15 - 14 15.2 System Configuration 15.2.7 Connecting to FP-M(C20TC) or FP-M(C32TC) ■1. When connecting to tool port or RS232C port PLC Connection cable Max. distance GOT Number of connectable equipment Model name Communication Type Cable model Connection diagram number Option device *3 Model FP-M(C20TC), FP-M(C32TC) (Tool port) RS-232 AFC8503(3m) *1 3m - (Built into GOT) 1 GOT for 1 PLC GT15-RS2-9P GT10-C02H- 6PT9P *2 AFC850…
177, 3.3 Connection Diagram 3 - 51 3 CONNECTION TO AZBIL (former YAMATAKE) CONTROL EQUIPMENT (19) RS485 connection diagram 19) *1 Pin No. of control equipment differs depending on the model. Refer to the following table *2 Terminating resistor should be provided for an Interface converter and a control equipment which will be terminals. *3 Connect FG grounding to the single-sided end of a cable shield line. *4 Set the terminating resistor of GOT as follows. Set the terminating resistor setting switch of the GOT main unit to &qu…
433, 10.6 Device Range that Can Be Set 10 - 21 CONNECTION TO SHINKO TECHNOS INDICATING CONTROLLER 10 10.6.1 SHINKO indicating controller (Shinko Technos Controller) *1 As bit specification of a word device is performed after the GOT reads the value, do not change the value with the indicating controller during this period. Device name Setting range Device No. representation Bit device The bit specification of the word device *1 Setting range of each word device - Word device Data item (..) ..0001 t…
339, Mitsubishi Electric GOT2000 Series 7.2 System Configuration 7 - 9 7 CONNECTION TO KOYO EI PLC ■2. When connecting to multiple PLCs *1 The data communications module is manufactured by KOYO ELECTRONICS INDUSTRIES CO., LTD. For details of the product, contact KOYO ELECTRONICS INDUSTRIES CO., LTD. *2 When the number of links exceeds 30, use a transmission line conversion unit D-01CV per 30 links. For details, refer to the following manual. ➠ KOYO EI PLC user's Manual *3 GT25-W, GT2505-V do…
188, Mitsubishi Electric GOT2000 Series 3 - 62 3.5 Control Equipment Side Setting 3.5.4 Connecting to SDC20/21, SDC30/31 ■1. Communication settings Make the communication settings by operating the key of the temperature controller. *1 The transmission speed setting must be consistent with that of the GOT side. *2 Do not set to "0". *3 Select the station address without overlapping with that of other units. 3.5.5 Connecting to CMC10L ■1. Communication settings Make the communication settings by operating the DIP switch of the Interface converter *1 The transmission speed …
465, 11.5 Controller Side Setting 11 - 31 CONNECTION TO CHINO CONTROLLER 11 (2) Transmission speed ■4. Setting by Switch (SW2) 11.5.9 Connecting to JU ■1. Key Lock setting To write the Digital and the Analog parameters, set the Key Lock setting. ■2. Communication settings Set the communication settings with controller key operation. *1 Avoid duplication of the station No. with any of the other units. *2 Adjust the settings with GOT settings. SW1-6 SW1-7 communication port Transmission speed OFF OFF Upper communication 9600bps OFF ON …
532, 15 - 2 15.1 Connectable Model List 15. CONNECTION TO PANASONIC INDUSTRIAL DEVICES SUNX PLC 15.1 Connectable Model List The following table shows the connectable models. *1 Any of the extension memory unit FP2-EM1, FP2-EM2 or FP2-EM3 is required. *2 The clock function is available for the AFP3210C-F, AFP3211C-F, AFP3212C-F and AFP3220C-F. *3 The GOT can only read the clock data.In the clock setting, though the adjust is available, the broadcast is not available. Model name Clock Communication Type Connectable GOT Refer to FP0-C1…
53, 1.3 Option Devices for the Respective Connection 1 - 25 1 PREPARATORY PROCEDURES FOR MONITORING ■4. When using a field network adapter unit A field network adapter unit can be installed in any position (1st to 3rd stage) of the extension interface. However, at the top of the field network adapter unit, you will not be able to mount the each communication unit. Example: Installing a field network adapter unit ■5. When using the sound output unit or ex…
322, 6 - 26 6.2 Serial Connection (b) When using KV-L20, KV-L21V • Terminator setting switch Set when carrying out RS-422 communication. Settings When multi-communication unit is a terminal When multi-communication unit is not a terminal ON OFF Terminator setting switch Port 1 (RS232) Port 2 (RS232/RS422/RS485) ON OFF …
5, A - 3 [DESIGN PRECAUTIONS] CAUTION Do not bundle the control and communication cables with main-circuit, power or other wiring. Run the above cables separately from such wiring and keep them a minimum of 100mm apart. Not doing so noise can cause a malfunction. Do not press the GOT display section with a pointed material as a pen or driver. Doing so can result in a damage or failure of the display section. When the GOT connects to an Ethernet netw…
511, Mitsubishi Electric GOT2000 Series 14 - 1 CONNECTION TO PANASONIC SERVO AMPLIFIER 14 14. CONNECTION TO PANASONIC SERVO AMPLIFIER 14.1 Connectable Model List . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 14 - 2 14.2 System Configuration . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 14 - 3 14.3 Connection Diagram. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 14 - 5 14.4 GOT Side Settings . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 14 - 11 14.5 Servo Amplifier Side Setting …
389, Mitsubishi Electric GOT2000 Series 8.6 Device Range that Can Be Set 8 - 23 8 CONNECTION TO JTEKT PLC 8.6.1 JTEKT PLC (JTEKT TOYOPUC-PLC) *1 Overlapped device designation of an input (X, EX, GX) and an output (Y, EY, GY), or a timer (T, ET) and a counter (C, EC) is not allowed.(Example: X0000 and Y0000, EX0000 and EY0000) *2 To store a setting value of T (timer) or C (counter), use TCS. Setting value of a timer and a counter is stored in TCS. (TCS cannot be used if a timer or a counter is not in a program.) *3 GX, GY, GM and EB can be used only in…
495, Mitsubishi Electric GOT2000 Series 12.4 Device Range that Can Be Set 12 - 21 CONNECTION TO TOSHIBA PLC 12 ■3. TOSHIBA PLC (Unified Controller nv Series) Device name Setting range Device No. representation Bit device External input (X) X000000 to X16383F Decimal +Hexadecimal External input (X) Y000000 to Y16383F Internal relay (R) R00000 to R8191F Input variable (I) I000000 to I16383F Output variable (Q) Q000000 to Q16383F Special relay (S) S00000 to S1023F Word device Extern…
369, 8.2 System Configuration 8 - 3 8 CONNECTION TO JTEKT PLC ■2. For the RS-232 connection (via an interface converter) *1 The link unit is a product manufactured by JTEKT Corporation. For details of the product, contact JTEKT Corporation. *2 The interface converter is a product manufactured by JTEKT Corporation. For details of the product, contact JTEKT Corporation. *3 GT25-W, GT2505-V does not support the option device. PLC Connectio…
397, 9.3 Connection Diagram 9 - 7 CONNECTION TO SHARP PLC 9 9.3 Connection Diagram The following diagram shows the connection between the GOT and the PLC. 9.3.1 RS-232 cable ■1. Connection diagram (1) RS-232 connection diagram 1) *1 GT27: CD, GT23: NC (2) RS-232 connection diagram 2) *1 GT27: CD, GT23: NC ■2. Precautions when preparing a cable (1) Cable length The maximum length of the RS-232 cable differs according to the specifications of the SHARP PLC. For details, refer to the following manual. …
572, 15 - 42 15.6 Device Range that Can Be Set 15.6 Device Range that Can Be Set The device ranges of controller that can be used for GOT are as follows. Note that the device ranges in the following tables are the maximum values that can be set in GT Designer3. The device specifications of controllers may differ depending on the models, even though belonging to the same series. Please make the setting according to the specifications of the controller actually used. W…
111, 2.6 Device Range that Can Be Set 2 - 35 2 CONNECTION TO IAI ROBOT CONTROLLER Word device Software Reset (SR) *2*5 SR0 Decimal Drive-Source Recovery (DSR) *2 DSR0 Origin return (RO) *7 RO0 to RO3 Point number specification movement (PNM) *7 PNM0 to PNM5 Operation stop/Cancel (OSC) *7 OSC0 to OSC2 Double word device Operation-Pause Reset (OPR) *2 OPR0 Servo (SV) *7 SV0 to SV2 Write to Flash ROM (FRW) *7 FRW0 to FRW1 Coordinate Affiliate Data 0 (CD0) *1 CD000:0 to CD000:F : CD0FF:0 to CD0FF:F Hexadecimal Coord…
253, Mitsubishi Electric GOT2000 Series 4.3 Ethernet Connection 4 - 51 4 CONNECTION TO OMRON PLC 4.3.3 GOT side settings ■1. Setting communication interface (Communication settings) Set the channel of the connected equipment. Step 1. Select [Common] [Controller Setting] from the menu. Step 2. The Controller Setting window is displayed. Select the channel to be used from the list menu. Step 3. Set the following items. • Manufacturer: OMRON • Controller Type: Varies w…
456, 11 - 22 11.3 Connection Diagram (12) RS485 connection diagram 12) *1 Pin No. of controller differs depending on the model. Refer to the following table. *2 Terminating resistor should be provided for a controller which will be terminating resistors. *3 Set the terminating resistor of The GOT side. ➠ ■3. Connecting terminating resistors *4 When connecting to DB1000 or DB200 Series, connect SG of the controller and SG of the GOT. *5 For KP2000 series, the terminal No. differs according to the model. *6 This indicates the symb…
420, 10 - 8 10.3 Connection Diagram 10.3 Connection Diagram The following diagram shows the connection between the GOT and the PLC. 10.3.1 RS-232 cable ■1. Connection diagram (1) RS-232 connection diagram 1) *1 Connect FG grounding to the appropriate part of a cable shield line. ■2. Precautions when preparing a cable (1) Cable length The length of the RS-232 cable must be 15m or less. (2) GOT side connector For the GOT side connector…
224, 4 - 22 4.2 Serial Connection ■2. When connecting to a serial communication board *1 Product manufactured by OMRON Corporation. For details on the product, contact OMRON Corporation. *2 When a GT10-C02H-6PT9P unit of the sub version A or B is used, do not ground the case of the D-sub (9-pin) connector. *3 GT25-W, GT2505-V does not support the option device. PLC Connection cable GOT Number of connectable equipment Model name Serial communica…
431, 10.5 Indicating Controller Side Setting 10 - 19 CONNECTION TO SHINKO TECHNOS INDICATING CONTROLLER 10 10.5.4 Station No. settings Set each station number so that no station number overlaps. The station number can be set without regard to the cable connection order. There is no problem even if station numbers are not consecutive. ■1. Direct specification When setting the device, specify the station number of the indicating controller of which data is to be changed. ■2. Indirect specification When setting the device, indirectly specify …
439, Mitsubishi Electric GOT2000 Series 11.2 System Configuration 11 - 5 CONNECTION TO CHINO CONTROLLER 11 11.2.2 Connecting to KP1000, KP2000, AL3000, AH3000 series ■1. When connecting to controller *1 Product manufactured by CHINO corporation. For details of the product, contact CHINO corporation. *2 GT25-W is not compatible to the option devices other than FA-LTBGT2R4CBL□□. *3 GT2505-V does not support the option device. Indicating controller Connection cable 1) Connection cable 2) Max. distance GOT Number of connectable equipment Model name Communication Type Cable…
176, 3 - 50 3.3 Connection Diagram (18) RS485 connection diagram 18) *1 Pin No. of control equipment differs depending on the model. Refer to the following table *2 Terminating resistor should be provided for an Interface converter and a control equipment which will be terminals. *3 Connect FG grounding to the single-sided end of a cable shield line. *4 Set the terminating resistor of GOT as follows. Set the terminating resistor setting switch of the GOT main unit to "Disa…
498, Mitsubishi Electric GOT2000 Series 13 - 2 13.1 Connectable Model List 13. CONNECTION TO TOSHIBA MACHINE PLC 13.1 Connectable Model List The following table shows the connectable models. Series Model name Clock Communication Type Connectable GOT Refer to TCmini Series TC3-01 RS-232 ➠ 13.2.1 TC3-02 TC6-00 TC8-00 TC5-02 RS-485 TC5-03 Robot controller TS2000 RS-232 ➠ 13.2.2 TS2100 …
VivoStick Stick PC's - #WKW9UZ
VivoStick, 2, asus/vivostick.pdf
All in One Printer Instruction #654542
X548 Family, 1, lexmark/x548-family.pdf
Wood heating solution Reference Book: SunMor SM-V30 (#EKVDV5)
SunMor SM-V30, 6, wood-heating-solution/sunmor-sm-v30.pdf
AudioBahn Guide: DUAL 2 OHM SERIES-SERIES - SCHEMA (#IR1MH5)
DUAL 2 OHM SERIES-SERIES - SCHEMA, 1, audiobahn/dual-2-ohm-series-series-schema.pdf
Microphone ULX-D Document, #9145TT
ULX-D, 27, shure/ulx-d.pdf
Two-Way Radio Tutorial #31O52Y
XT511, 28, midland/xt511.pdf
Title: J-STD-008 Compatible Single Access Wireless Terminal, Introductory Version. Document Number: PS-SAU-1900E Revision Number: 0.0 Release Date: Mar. 8th, 1999 Project Engineer: Y.S.Cho This document shows designs, technical data, and/or inventions which are the proprietary rights of Maxon America, Inc. and are disclosed in confidence to the recipient of t ...
ENGINEERING NOTE 090514_HDD POS to Perfection Senor Tech Pty Ltd ABN:54093127765 65 Weaver Street, Coopers Plains, QLD, 4108 Australia Telephone: +61 7 3275 5888 Facsimile: +61 7 3275 5800 www.senortech.com.au [email protected] Purpose / Warnings This document describes the Hard drive Removal & Replacement procedure for the ISPO ...
iSPOS series 8
• Large, easy-to-read 256 x 64 dot matrix display• Can display graphics, logos and Asian character sets• Vertical and horizontal scrolling of text and graphics• User-defined characters easily downloaded with built-in flash memory• Easy connectivity to a wide range of Epson POS products• Available in Epson Cool White and Epson Dark Gray EpsonDM-D500Customer DisplayEpson’s DM-D50 ...
MID TID Magnetic Stripe Card ReaderCANCEL key (Red)CLEAR key (Yellow)ENTER key (Green)FUNCtion keyPrinterCHQ (Green)SAV (Green)CR (Red)Paper FEED keyCHIP Card ReaderMAG Stripe Swipe CardCHIP Insert CardEFTPOS Quick Reference GuideANZ Merchant Services Support 1800 039 025 Credit Card Authorisation Centre 1800 999 205De ...
MODEL NUMBER: IMPROX TRT ImproX (TRT) Twin Remote Terminal INSTALLATION MANUAL SPECIFICATIONS Working Environment Open Frame Construction (XRT910) and Aluminium Cabinet (XRT911) Input Voltage Power Requirements Current (mA) Power (W) Power Supply Combo (IPS920) NOTE: The Power Supply Combo includ ...
IMPROX TRT 20
Instruction Leaet IL0131123ENEffective February 2016ContentsDescription PageGeneral information ........................2Instructions to assemble ....................4Installation instructions for Series NRX Type NF bus extension kit for 65 kA ﬁxed front connect breaker Instructions apply to:Series NRX Type NF frame (front connect) ULT 489 ...
Series NRX 8
|#||Brand||Model||Document Type/File||Pages||File Size||Last Checked|
Engage One Retail System 143
|#||Brand||Model||Document (PDF)||Pages||Size||Check Date|
BeanSpraut VGA Carabiner Camera